WU Chuan, YAN Bo, ZHANG Liang, ZHANG Bo, LI Qing. A Theoretical Algorithm for Jump Heights of Iced Transmission Lines After Ice Shedding[J]. Applied Mathematics and Mechanics, 2016, 37(2): 117-126. doi: 10.3879/j.issn.1000-0887.2016.02.001
 Citation: WU Chuan, YAN Bo, ZHANG Liang, ZHANG Bo, LI Qing. A Theoretical Algorithm for Jump Heights of Iced Transmission Lines After Ice Shedding[J]. Applied Mathematics and Mechanics, 2016, 37(2): 117-126.

# A Theoretical Algorithm for Jump Heights of Iced Transmission Lines After Ice Shedding

##### doi: 10.3879/j.issn.1000-0887.2016.02.001
Funds:  The National Natural Science Foundation of China(51277186)
• Rev Recd Date: 2015-11-04
• Publish Date: 2016-02-15
• An analytical model for multi-span transmission lines to estimate jump heights after ice shedding was set up, and an algorithm for the jump heights was developed by means of the energy equation, stress-sag relation, deformation and balance relation of the lines during the motion after ice shedding. The algorithm was verified through the comparison of the line jump heights determined respectively with the present algorithm, the finite element method and the Morgan theoretical algorithm. Furthermore, the present algorithm, the finite element method and the formula proposed in the Chinese design code for transmission lines were employed to evaluate the jump heights of typical transmission lines with different parameters after ice shedding, based on which the practicability of the present algorithm was discussed. It is indicated that the present algorithm could be used easily and quickly to determine the isolation clearance in the design of transmission lines located in icing zones.
•  [1] 刘和云. 架空导线覆冰防冰的理论与应用[M]. 北京: 中国铁道出版社, 2001.(LIU He-yun. Theories and Applications of Ice Cccretion and Anti-Icing on Overhead Transmission Lines[M]. Beijing: China Railway Publishing House, 2001.(in Chinese)) [2] 王璋奇, 齐立忠, 杨文刚, 王孟. 集中质量法模拟覆冰在架空线脱冰动张力实验中的适用性研究[J]. 中国电机工程学报, 2014,34(12): 1982-1988.(WANG Zhang-qi, QI Li-zhong, YANG Wen-gang, WANG Meng. Research on the applicability of lumped mass method for cable’s dynamic tension in the ice shedding experiment[J]. Proceedings of the CSEE,2014,34(12): 1982-1988.(in Chinese)) [3] Kollar L E, Farzaneh M. Modeling sudden ice shedding from conductor bundles[J]. IEEE Transactions on Power Delivery,2012,28(2): 604-611. [4] Jamaledding A, McClure G, Rousselet J, Beauchemin R. Simulation of ice-shedding on electrical transmission lines using Adina[J]. Computers & Structures,1993,47(4/5): 523-536. [5] Morgan V T, Swift D A. Jump height of overhead-line conductors after the sudden release of ice loads[J]. Proceedings of the Institution of Electrical Engineers,1964,111(10): 1736-1746. [6] MENG Xiao-bo, HOU Lei, WANG Li-ming, Mark M A , FU Guan-jun, SUN Bao-qiang, GUAN Zhi-cheng, HU Wei, CHEN Yong. Oscillation of conductors following ice-shedding on UHV transmission lines[J]. Mechanical Systems and Signal Processing,2012,30: 393-406. [7] Fekr M R, McClure G. Numerical modelling of the dynamic response of ice-shedding on electrical transmission lines[J]. Atmospheric Research,1998,46(1/2): 1-11. [8] 陈将, 严波, 陈科全. 重冰区架空输电线脱冰振动的数值模拟研究[J]. 重庆大学学报(自然科学版), 2007,30(S): 46-48.(CHEN Jiang, YAN Bo, CHEN Ke-quan. Numerical simulation of the dynamic response of ice-shedding on overhead electrical transmission in cold regions[J]. Journal of Chongqing University(Natural Science Edition),2007,30(S): 46-48.(in Chinese)) [9] 李黎, 夏正春, 付国祥, 梁政平. 大跨越输电塔-线在线路脱冰作用下的振动[J]. 振动与冲击, 2008,27(9): 32-34.(LI Li, XIA Zheng-chun, FU Guo-xiang, LIANG Zheng-ping. Ice-shedding induced vibration of a long-span electric transmission tower-line system[J]. Journal of Vibration and Shock,2008,27(9): 32-34.(in Chinese)) [10] YAN Bo, CHEN Ke-quan, GUO Yue-ming, LIANG Ming, YUAN Qi. Numerical simulation study on jump height of iced transmission lines after ice shedding[J]. IEEE Transactions on Power Delivery,2013,28(1): 216-225. [11] 陈勇, 胡伟, 王黎明, 侯镭. 覆冰导线脱冰跳跃特性研究[J]. 中国电机工程学报, 2009,29(28): 115-121.(CHEN Yong, HU Wei, WANG Li-ming, HOU Lei. Research on ice-shedding characteristic of icing conductor[J]. Proceedings of the CSEE,2009,29(28): 115-121.(in Chinese)) [12] 候镭, 王黎明, 朱谱轩, 关志成. 特高压线路覆冰脱落跳跃的动力计算[J]. 中国电机工程学报, 2008,28(6): 1-6.(HOU Lei, WANG Li-ming, ZHU Pu-xuan, GUAN Zhi-cheng. Dynamic behavior computation of ice shedding of UHV overhead transmission lines[J]. Proceedings of the CSEE,2008,28(6): 1-6.(in Chinese)) [13] 杨风利, 杨靖波. 重冰区覆冰导线脱冰跳跃荷载分析[J]. 振动与冲击, 2013,32(5): 10-15.(YANG Feng-li, YANG Jing-bo. Analysis on loads form ice shedding conductors in heavy icing areas[J]. Journal of Vibration and Shock,2013,32(5): 10-15.(in Chinese)) [14] Kollár L E, Farzaneh M, Van Dyke P. Modeling ice shedding propagation on transmission lines with or without interphase spacers[J]. IEEE Transactions on Power Delivery,2013,28(1): 261-267. [15] Mirshafiei F, McClure G, Farzaneh M. Modelling the dynamic response of iced transmission lines subjected to cable rupture and ice shedding[J]. IEEE Transactions on Power Delivery,2013,28(2): 948-954. [16] Oertli H. Oscillations de cables electriques aeriens apres la chute de surcharges[J]. Bull Assoc Suisse Elect,1950,41: 501. [17] Lips K. Die Schnellhohe von Freileitungsseilen nach abfallen von Zusatzlastcn[J]. Bull Assoc Suisse Elect,1952,43: 62. [18] 邵天晓. 架空送电线路的电线力学计算[M]. 第2版. 北京: 中国电力出版社, 2003: 185-188.(SHAO Tian-xiao. Mechanics Calculation of Overhead Transmission Lines[M]. 2nd ed. Beijing: China Electric Power Press, 2003: 185-188.(in Chinese)) [19] 张殿生. 电力工程高压送电线路设计手册[M]. 第2版. 北京: 中国电力出版社, 2003.(ZHANG Dian-sheng. Design Manual of High Voltage Transmission Lines for Electric Engineering[M]. 2nd ed. Beijing: China Electric Power Press, 2003.(in Chinese)) [20] Barbieri N, de Souaz Júnior O H, Barbieri R. Dynamic analysis of transmission line cables—part 2: damping estimation[J]. Mechanical Systems and Signal Processing,2004, 18(3): 671-681.

### Catalog

###### 通讯作者: 陈斌, bchen63@163.com
• 1.

沈阳化工大学材料科学与工程学院 沈阳 110142